The cold water in the cooling tower enters the inner plate heat exchanger of the liquid freezer through the water pump, main pipe and branch pipe, exchanges heat with the hot oil inside, then turns into hot water, and then flows back to the cooling tower for cooling through the branch pipe and main pipe, and then flows into the plate heat exchanger for heat exchanging circulation. The hot oil of the plate heat exchanger in the liquid cooling cabinet becomes low temperature oil after exchanging heat with the cold water, and then flows back to the tank of the liquid cooling cabinet to cool the server. After exchanging heat with the server, it becomes high temperature oil again, and enters the plate heat exchanger again through the oil pump for heat exchanging circulation.
—High temperature protection aystem, automatically cut off power when it is higher than 50 degrees
—Hot oil and cold water heat exchange syatem, to ensure that the hot oil is cooled down to cold in time
—Power distribution and network connection system
What do you need ?
(These products are not included)
estimated price 390USD
10Ton Water tower
estimated price 200USD
1.5KW Water Pump
estimated price 170USD
total cost (USD) :
estimated price 760 USD
|Find these items in your country|
Want to increase Hashrate ?
PSU APW12 6000/7000W For Overlocking:
Cable for 16A :
—Before use, the inlet and outlet water pipes and the pool shall be thoroughly rinsed to eliminate the garbage in the tower to prevent the pipeline from being blocked.
—Do not use river water or water with impurities in water cooling towers, which may cause clogging of pipes and panels.
—When using tap water to inject water, it is necessary to add the corresponding softener according to the local tap water quality to prevent pipe scaling and blockage.
—After the fan is working, open the water valve and adjust the flow rate of the pump at the same time. The water pressure, current, voltage, vibration, and noise values entering the tower should be within the specified range, and the tone values should be within the specified range.
—The circulating water should be tap water or clean water, not contain oil and impurities, and the turbidity should not exceed 50mmg/l.
—As essential cooling equipment, the water cooling tower should be managed by a particular person and make a record of the inlet and outlet water temperature, flow, and meteorological parameters of the cooling tower.
—For cold weather countries, antifreezing oil should be prepared to avoid the pipe breaking